October 31, 1996
The Chicago Regional Office has brought to our attention the potential for feed water pipes in electrical power generation facilities to rupture causing hazardous release of steam and hot water. During an investigation of a multiple fatality accident at an electrical power generation facility in an industrial plant, the Appleton Area Office uncovered at least three other feed water pipe failure incidents in other power plants. In two of the three incidents, six additional fatalities had occurred. In all cases, the feed water pipe failures were attributed to wall thinning as a result of single-phase erosion/corrosion, leading to rupture of the pipes under high working pressures.
The rupture of feed water pipes due to wall thinning creates the potential for serious burns, massive property damage, and power outages in electrical power generation plants. These feed water pipe failures could not be linked to any specific aspect of system designs, materials, or operating histories to support a conclusion that single-phase erosion/corrosion was distinctive to these particular power plants. This suggests that these may not be isolated incidents but a problem that may be widespread in the industry.
Several factors affect the rate of erosion/corrosion in piping. These factors include material composition of carbon steel piping, temperature, low water pH, low dissolved oxygen content, pipe geometry, and fluid velocity. The flow path through elbows, bends, tees, orifices, welds, valves, and backing rings creates turbulence in flow which, with fluid velocity, has the potential to react with the protective oxide layer of carbon steel piping, contributing to the erosion/corrosion process.
Feed water pipes are addressed in the standard boiler inspection. Generally only a visual inspection with the pipe insulation in place is done or required. Since this will not reveal pipe thinning, employers may not have actual knowledge of the pipe wall thinning that could be occurring.
To minimize the potential for personal injury or loss of life, property damage, and power interruptions resulting from feed water pipe failure, it is recommended that employers of electrical power generation facilities establish a flow-assisted corrosion (FAC) program:
For additional information on FAC, the following documents are suggested:
Please distribute this bulletin to all Area Offices, State Plan States, Consultation Project Offices, and appropriate labor and industry groups.
1 The Directorate of Technical Support issues Hazard Information Bulletins (HIBs) in accordance with OSHA Instruction CPL 2.65 to provide relevant information regarding unrecognized or misunderstood health hazards, inadequacies of materials, devices, techniques, and safety engineering controls. HIBs are initiated based on information provided by the field staff, studies, reports, and concerns expressed by safety and health professionals, employers, and the public. Bulletins are developed based on a thorough evaluation of available facts in coordination with appropriate parties.
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.