Electric Power Generation, Transmission and Distribution Standard
Minimum Approach Distance Calculator
You can use this page to calculate minimum approach distances for phase-to-phase system voltages exceeding 72.5 kilovolts in accordance with 29 CFR 1910.269 and 29 CFR Part 1926, Subpart V, as follows:
- Select the method of measurement (feet or meters);
- Enter the maximum phase-to-phase system voltage, the maximum transient overvoltage resulting from an engineering analysis of the system, and the elevation of the worksite;
- Check the appropriate boxes to indicate "yes" answers to the questions, or uncheck them to indicate "no."
The calculator provides the minimum approach distance, in feet or meters (depending on your selection), for phase-to-ground and phase-to-phase exposures.
Footnote (1) Enter the maximum anticipated per-unit transient overvoltage, phase-to-ground, determined through an engineering analysis or assume a maximum anticipated per-unit transient overvoltage, phase-to-ground, in accordance with the following table:
|Voltage range (kV)||Assumed maximum per-unit transient overvoltage|
|72.6 to 420.0||3.5|
|420.1 to 550.0||3.0|
|550.1 to 800.0||2.5|