Shipping drums and containers shall not be pressurized to remove their contents.
A temporarily assembled pressurized piping system conveying hazardous liquids or gases shall be
provided with a relief valve and by-pass to prevent rupture of the system and the escape of such hazardous liquids or gases.
Pressure vessels, drums and containers containing toxic or flammable liquids or gases shall not be
stored or used where they are subject to open flame, hot metal, or other sources of artificial heat.
Unless pressure vessels, drums and containers of 30 gallon capacity or over containing flammable or
toxic liquids or gases are placed in an out-of-the-way area where they will not be subject to physical injury from an outside source, barriers or
guards shall be erected to protect them from such physical injury.
Containers of 55 gallons or more capacity containing flammable or toxic liquid shall be surrounded by
dikes or pans which enclose a volume equal to at least 35 percent of the total volume of the containers.
Fire extinguishers adequate in number and suitable for the hazard shall be provided. These
extinguishers shall be located in the immediate area where pressure vessels, drums and containers containing flammable liquids or gases are stored or
in use. Such extinguishers shall be ready for use at all times.