Standard Interpretations - Table of Contents|
| Standard Number:||1926.500|
March 20, 1986
Mr. Thomas P. Brantley
Bradenton Wastewater Treatment
Plant & Improvements
Post Office Box 70
Bradenton, Florida 33506
Dear Mr. Brantley:
This is in response to your letter of March 5, requesting a clarification of our design criteria for a standard railing as required in 29 CFR 1926.500(f)(1)(iii) through (vi). Your letter addressed to Mr. Allan E. Martin was forwarded to this office of response. This also confirms your telephone conversation with a member of my staff on March 13.
29 CFR 1926.500(f)(1)(iv) requires that the anchoring of parts and framing of members for railings of all types shall be of such construction that the completed structure shall be capable of withstanding a load of at least 200 pounds applied in any direction at any point on the top rail, with a minimum of deflection. The 200 pound force is considered as a single concentrated load acting at any point on the top rail, with a minimum of deflection. This usually allows a load reduction at the posts due to the transmission of the load through the top railing.
29 CFR 1910.23(e) includes the same design criteria for guardrail systems to be used in general industry.
If we can be of further assistance, please do not hesitate to let us know.
John B. Miles, Jr., Director
Directorate of Field Operations
|Standard Interpretations - Table of Contents|
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.