Standard Interpretations - Table of Contents|
| Standard Number:||1926.500; 1926.451|
July 24, 1984
Mr. B. J. Newton
Territory Safety Coordinator
Turner Construction Company
55 West Monroe Street
Chicago, Illinois 60603
Dear Mr. Newton:
This is in response to your letter of June 29, concerning the acceptability of wire rope and/or cable as a method of perimeter protection for a building under construction.
The use of wire ropes as top rails and intermediate rails of guardrail systems used for perimeter protection or for guardrails used on scaffolding meeting the equivalent requirements of 29 CFR 1926.500(d)(1) and 29 CFR 1926.451(a)(5) is acceptable provided it meets the following guidelines:
(1) Wire rope shall be secured to each support and taut at all times.
(2) The wire rope shall be free of sharp edges, burrs, or projections which may be a hazard.
(3) The maximum deflection of the top rail when a load of 200 pounds is applied in any direction at any point on the top rail shall not exceed 3 inches in one direction which includes the free hanging sag in the wire rope.
Our compliance officers are aware that wire rope is an acceptable method of perimeter protection for buildings under construction.
If we can be of further assistance, please let use know.
John B. Miles, Jr., Director
Directorate of Field Operations
|Standard Interpretations - Table of Contents|
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.