Standard Interpretations - Table of Contents|
| Standard Number:||1910.110(b)(6)|
29 CFR 1910.110(b)(6)
February 10, 1975
Mr. E. R. Bentley
Cummins Sales, Inc.
10470 Evendale Drive
Cincinnati, Ohio 45241
Dear Mr. Bentley:
We are in receipt of your letter dated January 20, 1975, in which you supplied additional information relative to your application for variance from Section 1910.110(b)(6) Storage and Handling of Liquefied Gas - Table H-23, of the Occupational Safety and Health Standards.
You have stated that you have two (2) 500 gallon propane gas tanks located ten (10) feet from one of your buildings. These tanks are separated from each other by three (3) feet. You further state that this does not meet the distances requirements of the above standard. It is from this requirement that a variance is sought.
The requirements of Table H-23 are based on the water capacity per container. The exception to this rule are those containers having a water capacity of less than 125 gallons which are figured in the aggregate amount as delineated in Note 1 of the table. Your containers are based on the per container rule, therefore, the present location of your two (2) 500 gallon containers does meet the requirements of Table H-23 (copy of Table H-23 enclosed).
No further action will be taken on your variance application.
Barry J. White
Associate Assistant Secretary for
|Standard Interpretations - Table of Contents|
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.