Standard Cited: 5A0001 OSH Act General Duty Paragraph
|Nr: 122375512||Citation: 02064||Issuance: 07/12/1996||ReportingID: 0112900|
|Viol Type:||Willful||NrInstances:||6||Contest Date:||07/23/1996|
|Abatement Date:||08/17/1996 X||Nr Exposed:||4||Final Order:||08/18/1997|
|Current Penalty:||$20,800.00||Gravity:||03||Haz Category:||ELECTRIC|
|Penalty and Failure to Abate Event History|
|Penalty||F: Formal Settlement||08/18/1997||$20,800.00||08/17/1996||Willful|
Text For Citation: 02 Item/Group: 064 Hazard: ELECTRIC
Section 5(a)(1) of the Occupational Safety and Health Act of 1970: The employer did not furnish employment and a place of employment which were free from recognized hazards that were causing or likely to cause death or serious physical harm to employees in that employees housed in trailer #2 were exposed to the hazards of fire, smoke inhalation, electric shock and electrocution: a)North Entrance - The one-bulb light fixture, which was mounted on the outside wall, was not properly secured in place and was not provided with strain relief. b)Kitchen - The three-bulb light fixture had one light bulb and assembly was not secured in place and was not provided with strain relief. c)Hall - The one-bulb light fixture bracket was not secured in place and the conductors were not provided with strain relief. d)Bathroom - The two-bulb light fixture was not secured in place and was not provided with strain relief. e)Kitchen - The Philco refrigerator was not grounded, and the metal frame of the refrigerator contained 39 volts. f)Hall - The battery powered smoke detector and alarm was not operational. Among other methods, one feasible means of abatement would be to provide electrical installations which are in compliance with the National Electrical Code.
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.