Standard Cited: 5A0001 OSH Act General Duty Paragraph
|Nr: 122375512||Citation: 02042||Issuance: 07/12/1996||ReportingID: 0112900|
|Viol Type:||Willful||NrInstances:||9||Contest Date:||07/23/1996|
|Abatement Date:||08/17/1996 X||Nr Exposed:||4||Final Order:||08/18/1997|
|Current Penalty:||$20,800.00||Gravity:||03||Haz Category:||ELECTRIC|
|Penalty and Failure to Abate Event History|
|Penalty||F: Formal Settlement||08/18/1997||$20,800.00||08/17/1996||Willful|
Text For Citation: 02 Item/Group: 042 Hazard: ELECTRIC
Section 5(a)(1) of the Occupational Safety and Health Act of 1970: The employer did not furnish employment and a place of employment which were free from recognized hazards that were causing or likely to cause death or serious physical harm to employees in that employees housed in trailer #33 were exposed to the hazards of fire, smoke inhalation, electric shock and electrocution: a)Hall - The one-bulb light fixture did not have a permanent and continuous path to ground. b)Southwest Bedroom - The two-bulb light fixture did not have a permanent and continuous path to ground. c)Northeast Bedroom - The two-bulb light fixture did not have a permanent and continuous path to ground. d)Kitchen - The two-bulb light fixture did not have a permanent and continuous path to ground. e)West Entrance - The outdoor light fixture was cracked and the metal frame did not have a permanent and continuous path to ground. f)Hall - The circuit-breaker panel, supplying power to the trailer, was not provided with a blank or knockout exposing live electrical parts to accidental contact. g)Northwest Bedroom - The electrical outlet, which was mounted on the northwest wall, contained an open ground. h)Kitchen - The electrical outlet, which was mounted above the counter-top, contained an open ground. i)Dining Area - The electrical outlet, which was mounted on the south wall, was not provided with a cover or faceplate exposing live electrical parts to accidental contact. Among other methods, one feasible means of abatement would be to provide electrical installations which are in compliance with the National Electrical Code.
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.