Standard Cited: 5A0001 OSH Act General Duty Paragraph
|Nr: 110416880||Citation: 02055||Issuance: 08/29/1991||ReportingID: 0625700|
|Viol Type:||Willful||NrInstances:||3||Contest Date:|
|Abatement Date:||10/06/1991 X||Nr Exposed:||1||Final Order:|
|Current Penalty:||$17,750.00||Gravity:||05||Haz Category:||EXPLOSION|
|Penalty and Failure to Abate Event History|
|Penalty||I: Informal Settlement||08/29/1991||$17,750.00||10/06/1991||Willful|
Text For Citation: 02 Item/Group: 055 Hazard: EXPLOSION
Section 5(a)(1) of the Occupational Safety and Health Act of 1970: The employer did not furnish employment and a place of employment which was free from recognized hazards that were causing or likely to cause death or serious physical harm to employees by exposing them to serious fire and explosion hazards. %% (a) On or about March 3, 1991, the main block valve at the bottom of the F-7 was closed with prevented water from draining out of the CUU "A" during the start-up procedure. Consequently, hot oil was mixed with water, in the F-7 Slurry Settling Drum for the CUU "A", thereby causing a catastrophic failure of the slurry settling drum, releasing flammable and combustable liquids, gases, and vapors. %% NOTE: A feasible and useful method among others of correcting this hazard is to provide a strickly enforce the use of a detailed written start-up procedure with signed and dated logs for specific task(s). %% (b) Employer did not comply with the applicable provisions of the API 510, ASME Boiler and Pressure Vessel Code, Section V, Vii, and IX and American Society for Nondestructive Testing, Code for Qualifications of Welders, Welding Inspectios, and Pressure Vessel Inspectors including, but not limited to, API 510, Section 5, Paragraph 5.2.1; ASME Boiler and Pressure Vessel Code, Section IX, Welding and Brazing Qualifications Section V, Paragraph 2.2 and American Society for Nondestructive Testing, Parts 5 and 6, thereby exposing employees to the hazard of inadequate welds on pressure vessels. NOTE: A feasible and useful method among others of correcting this hazard is to ensure that persons who are authorized to perform and interpret Non-Destructive Testing (NDT) are qualified to American Society of Non-Destructive Testing (ASNT) SNT-TC-14 or equivalent written requirements or written procedures in accordance with ASME Boiler and Pressure Vessel Code, Section V, 1989.
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.