- Part Number:1910
- Part Number Title:Occupational Safety and Health Standards
- Subpart:1910 Subpart H
- Subpart Title:Hazardous Materials
- Standard Number:
- Title:Additional requirements for dipping and coating operations that use flammable liquids or liquids with flashpoints greater than 199.4 °F (93 °C).
- GPO Source:
If you use flammable liquids, you must comply with the requirements of this section as well as the requirements of §§ 1910.123, 1910.124, and 1910.126, as applicable.
|You must also comply with this section if:||And:|
If the ventilation rate drops below what is required by paragraph (b) of § 1910.124.
All electrical wiring and equipment conform to the applicable hazardous (classified)-area requirements of subpart S of this part (except as specifically permitted in paragraph (g) of § 1910.126); and
Is installed in accordance with NFPA 86A-1969, Standard for Ovens and Furnaces (which is incorporated by reference in § 1910.6 of this part);
You must prohibit smoking in a vapor area and must post a readily visible "No Smoking" sign near each dip tank.
Manual fire extinguishers that are suitable for flammable and combustible liquid fires and that conform to the requirements of § 1910.157; and
At least 100 °F (37.8 °C) below the liquid's autoignition temperature.
[64 FR 13909, March 23, 1999; 77 FR 17777, March 26, 2012]