Regulations (Standards - 29 CFR) - Table of Contents|
| Part Number:||1910|
| Part Title:||Occupational Safety and Health Standards|
| Subpart Title:||Fire Protection|
| Standard Number:||1910.161|
| Title:||Fixed extinguishing systems, dry chemical.|
| GPO Source:||e-CFR|
Scope and application. This section applies to all fixed extinguishing systems, using dry chemical as the extinguishing agent, installed to meet a particular OSHA standard. These systems shall also comply with 1910.160.
The employer shall assure that dry chemical agents are compatible with any foams or wetting agents with which they are used.
The employer may not mix together dry chemical extinguishing agents of different compositions. The employer shall assure that dry chemical systems are refilled with the chemical stated on the approval nameplate or an equivalent compatible material.
When dry chemical discharge may obscure vision, the employer shall provide a pre-discharge employee alarm which complies with 1910.165 and which will give employees time to safely exit from the discharge area prior to system discharge.
The employer shall sample the dry chemical supply of all but stored pressure systems at least annually to assure that the dry chemical supply is free of moisture which may cause the supply to cake or form lumps.
The employer shall assure that the rate of application of dry chemicals is such that the designed concentration of the system will be reached within 30 seconds of initial discharge.
[45 FR 60712, Sept. 12, 1980]
Next Standard (1910.162)|
|Regulations (Standards - 29 CFR) - Table of Contents|
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.