Regulations (Standards - 29 CFR) - Table of Contents|
| Part Number:||1910|
| Part Title:||Occupational Safety and Health Standards|
| Subpart Title:||Occupational Health and Environmental Control|
| Standard Number:||1910.95 App D|
| Title:||Audiometric test rooms|
| GPO Source:||e-CFR|
This Appendix is Mandatory
Rooms used for audiometric testing shall not have background sound pressure levels exceeding those in Table D-1 when measured by equipment conforming at least to the Type 2 requirements of American National Standard Specification for Sound Level Meters, S1.4-1971 (R1976), and to the Class II requirements of American National Standard Specification for Octave, Half-Octave, and Third-Octave Band Filter Sets, S1.11-1971 (R1976).
TABLE D-1 - MAXIMUM ALLOWABLE OCTAVE-BAND SOUND PRESSURE LEVELS FOR AUDIOMETRIC TEST ROOMS _______________________________________________________________ Octave-band center frequency (Hz)............... 500 1000 2000 4000 8000 Sound pressure level (dB) ... 40 40 47 57 62 _______________________________________________________________
Next Standard (1910.95 App E)|
|Regulations (Standards - 29 CFR) - Table of Contents|
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.