Standard Interpretations - (Archived) Table of Contents|
| Standard Number:||1910.305|
June 11, 1993
Mr. Rick Cee
U.S. Department of Labor
Occupational Safety and Health
Salt Lake City Technical Center
1781 South 300 West
Salt Lake City, UT 84165-0200
Dear Mr. Cee:
This is in response to your letter of February 26, regarding the use of "power strips". You apparently want our opinion on whether certain working conditions relative to the described "power strips" might constitute a violation of OSHA standards. You were also concerned about the cost of abatement should a violation exist. Please accept our apologies for the delay in the response.
"Power strips" as mentioned in your letter or "surge/noise protective strips" as termed in the literature you sent as enclosures are generally referred to as temporary power taps. Temporary power taps that incorporate switches, indicator lights, filters for electromagnetic interference, fuses, varistors, or other overcurrent mechanisms in their design could be devices for transient voltage surge suppression of equipment. Transient voltage surge suppressors when used to preserve the components of the equipment listed in your letter (computer, printer, fax, miscellaneous appliances and analytical instruments) could be considered a device as defined in 29 CFR 1910.399:
Device. A unit of an electrical system which is intended to carry but not utilize electric energy.
If the temporary power taps are being used to provide transient voltage surge suppression, then these devices would meet the OSHA standards. If the temporary power taps are being used solely as wiring to provide extra or more convenient outlets, then this is a violation of 29 CFR 1910.305(g)(1)(iii)(A):
... flexible cords and cables may not be used:
(A) As a substitute for the fixed wiring of a structure;....
The selection of the surge/noise protective devices should be made following the manufacturer's recommendations for each piece of equipment that is to have this safeguard. An assessment of the electric branch circuits in the facility should be made to assure there is no potential for an electric overload situation where the equipment is used.
If you should need further assistance please do not hesitate to contact us.
Raymond Donnelly, Director
Office of General Industry Compliance
|Standard Interpretations - (Archived) Table of Contents|
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.