Standard Interpretations - (Archived) Table of Contents|
| Standard Number:||1910.151|
September 9, 1992
R. DAVIS LAYNE
PATRICIA K. CLARK, DIRECTOR
Interpretation of 29 CFR 1910.151(c) with respect to the OPTI-KLENS Eyewash Fountain
This is in response to your memorandum of July 24, on the subject matter.
The MET Electrical Testing Company, Inc., (MET), one of the National Recognized Testing Laboratories (NRTL's) accepted by the Occupational Safety and Health Administration (OSHA), has tested the OPTI-KLENS Eyewash Fountain.
The results of their test, #ESL0101, were issued August 19, 1992, and a copy is attached for your files. The conclusion states that the OPTI-KLENS Eyewash Fountain system complies with regulations of ANSI Z358.1, 1990 Edition. Although OSHA does not require NRTL verification on eyewash fountains, OSHA accepts satisfactory results of NRTL tests conducted on products as proof that the products meet recognized test standard requirements.
Your first specific concern was that two steps are required to operate the OPTI-KLENS Eyewash Fountain: turning on the faucet and then activating the unit. Since the conclusion of the NRTL test was that the OPTI-KLENS Eyewash Fountain can be activated in an average time of 0.78 seconds, the compliance officer may have to run time lapse tests to document a violation.
Your second stated concern was that the unit is connected in such a way that the injured employee may turn on the hot water. If injury to the eyes can be caused due to hot water, then a citation is appropriate.
|Standard Interpretations - (Archived) Table of Contents|
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.