Standard Interpretations - (Archived) Table of Contents|
| Standard Number:||1910.303(a); 1926.403(a)|
DATE: June 12, 1991 MEMORANDUM FOR: AREA DIRECTORS DISTRICT SUPERVISORS FROM: LINDA R. ANKU REGIONAL ADMINISTRATOR SUBJECT: Extension Cords Acceptable for Use
Only extension cords (cord sets) that are approved, as an assembly, by a Nationally Recognized Testing Laboratory (NRTL) such as UL are permitted to be used at places of employment. This limitation is based on the requirement that all equipment be approved as set forth in 29 CFR 1910.303(a) and 29 CFR 1926.403(a).
There are a large number or extension cords purchased and used by employers that are not approved for use by a NRTL. This is particularly a problem on construction sites. There are extension cords used on these sites that are referred to by the manufacturer as contractor or handyman cords but they are not approved.
Currently UL approves most extension cords. When UL approves equipment it is marked with the UL label and on that label will be the name of the equipment or the assembly that is approved. This is an important point because the presence of a UL label on a piece of equipment does not necessarily mean that the entire assembly the equipment is part of is approved. In many cases the UL label only means that one component of the assembly is approved; not that the entire assembly is approved. The cord, attachment cap (plug), or receptacle portion of the extension cord could be approved but the entire assembly that is the extension cord would not have a UL approval unless it was so marked. Therefore, such a cord would not be acceptable.
The danger associated with the use of extension cords that are not approved is that such cords may not be constructed properly or they may not be appropriate for the environment in which they are being used. A listing or approval of equipment by a NRTL substantially reduces the possibility of such problems.
Employers supplying unapproved cords for their employees use should be cited. A reasonably predictable injury for this type of a violation would be electrical shock.
If you have any questions regarding this matter, please contact John McFee at FTS 596-1201.
|Standard Interpretations - (Archived) Table of Contents|
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.