Standard Interpretations - Table of Contents|
| Standard Number:||1926.404(b)(1)|
April 18, 1991
Mr. William Dillon
Virginia Occupational Safety & Health
Commonwealth of Virginia
Department of Labor and Industry
205 North Fourth Street
P.O. Box 12064
Richmond, Virginia 23241
Dear Mr. Dillon:
This letter is in response to the following questions from John Crisanti:
1) Does Federal OSHA consider extension cords, connected to the permanent wiring of a building on a construction site, to be temporary wiring?
2) Are the receptacles on such cords required to be protected by GFCIs or an assured equipment grounding program?
The response to both questions is "Yes". OSHA Standards 29 CFR 1926.404 (b)(1)(i)- (iii) require that such extension cord sets be protected by GFCIs or an assured equipment grounding program.
This response is based on specific guidance contained in the preamble to the Final rule for Electrical Standards for Construction (29 CFR 1926.400-449); which was published in the Federal Register on July 11, 1986.
The following pertinent statement from page 25310 of the referenced Federal Register, a copy of which is enclosed, clearly stated OSHA's intent on this matter:
"For example, under the OSHA regulation for GFCIs, protection must be provided for the receptacles on the end of extension cord sets even if the extension cords are supplied by permanent wiring".
If you require any additional information regarding this matter, please contact John McFee of my staff at 215-596-1201.
LINDA R. ANKU
.....EXCERPT FROM FEDERAL REGISTER
Vol. 51, No. 133, Friday, July 11, 1986 Page 25310
Section 1926.404 Wiring design and protection.
For example, under the OSHA regulation for GFCIs, protection must be provided for the receptacle outlets on the end of extension cord sets even if the extension cords are supplied by permanent wiring. Under the NEC, GFCI protection is only required when temporary wiring is used and all the requirements for running temporary wiring (Article 305 of the 1984 NEC) are met. Other significant differences exist between the OSHA and NEC requirements for the assured equipment grounding conductor program. Since the OSHA regulation provides greater employee protection, compliance with analogous 1984 NEC provisions alone will not be acceptable under Subpart K.
|Standard Interpretations - Table of Contents|
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.