Standard Interpretations - (Archived) Table of Contents|
| Standard Number:||1910.309|
July 26, 1979
Mr. John Schreiner
Executive Vice President
Vacuum Instrument Corporation
6 Stepar Place
Huntington Station, New York 11746
Dear Mr. Schreiner:
This is in response to your recent inquiry to Donald Shay requesting an opinion concerning the installation of electrical equipment.
Section 110-16(a) of the 1971 National Electric Code (NEC) requires the work space shall be at least 30 inches wide in front of the electrical equipment. Distances are to be measured from the live parts, if such are exposed or from the enclosure front or opening when such are enclosed.
The electrical equipment installed as indicated on the drawing identified as sheet #1 measuring 30 inches from the enclosed front of the panel to the conveyor, appears to comply with the intent of 29 CFR 1910.309 which references the 1971 NEC.
I hope this information will be helpful to you. If I may be of any further assistance, please feel free to contact me.
Grover C. Wrenn Director,
and State Programs
|Standard Interpretations - (Archived) Table of Contents|
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.