Standard Interpretations - (Archived) Table of Contents|
| Standard Number:||1910.178|
May 5, 1977
Mr. William Rubenzer
Storage Battery Service Co. Inc.
106 E. Melvina St.
Milwaukee, Wisc. 53212
Subject: 1910.178(g) Changing and Charging Storage Batteries
Reference: Your memo of 4/21/77
Dear Mr. Rubenzer:
The standards are silent on the material to be used, or not to be used. (g)(4) - A conveyor, overhead hoist, or equivalent material handling equipment shall be provided for handling batteries.
(g)(3) states that when racks are used for support of batteries, they should be made of a material nonconductive to spark generation or be coated or covered to achieve this objective.
The source of the Federal Standard is ANSI B56.1 1969 Powered Industrial Truck and NFPA 505-1969. In reviewing the 1975 revision of NFPA 505 Section 4.3 charging and changing storage batteries "chain hoists shall be equipped with load-chain containers. When hand hoist is used, uncovered batteries shall be covered with a sheet of plywood or other nonconducting material to prevent the hand chain from shorting on cell connectors or terminals. A properly insulated spreader bar shall be used with any overhead hoist". The above section also appears in the source standard.
Although the above section was not promulgated as an OSHA Standard, it is a consensus of the writers of the NFPA Standard that, a properly insulated spreader bar shall be used with any overhead hoist, whether the battery is covered or not.
Please feel free to call us at anytime. 800-621-0523
EDWARD J. LARGENT
Assistant Regional Administrator
for Technical Support
|Standard Interpretations - (Archived) Table of Contents|
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.