Standard Interpretations - (Archived) Table of Contents|
| Standard Number:||1910.37|
February 16, 1977
Mr. Daniel R. Magnier
New York Telephone
2 Pennsylvania Plaza
New York, New York 10001
Dear Mr. Magnier:
This is in response to your letter requesting clarification of the OSHA Standard 1910.37(q)(6), the last sentence of which requires colored location indicating lights.
According to your letter with an enclosure of an OSHA Standards Notice reproduced in a magazine, there was a proposal to delete the last sentence of 1910.37(q)(6) requiring colored location indicating lights. However, the reproduced article indicated that there was a cancellation date for this notice of July 1, 1974. In looking at the 1976 Volume of the 1910 Standard, we note that the last sentence of 1910.37(q)(6) states, "Artificial light giving illumination to exit signs other than the internally illuminated type shall have screens, discs, or lenses, of not less than 25 square inches area made of translucent material to show red or other specified designating color on the side of the approach." This indicates that there has been no change in the Standard and that the sentence in question has not been deleted. Since that is a fact, then externally illuminated exit signs must be provided with a designating screen lighted with five (5) foot candles on the surface of the exit sign in accordance with the standard.
Please feel free to contact us if there are further questions about OSHA standards.
Occupational Safety and Health Administration
|Standard Interpretations - (Archived) Table of Contents|
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.