Standard Interpretations - Table of Contents|
| Standard Number:||1910.178(g)(2)|
January 26, 1976
Mr. John R. Reilly
Corporate Safety Director
Fisher Scientific Company
711 Forbes Avenue
Pittsburgh, PA 15219
Dear Mr. Reilly:
Your letter of January 16, 1976 requested definition of the phrase "Adequate ventilation" as used in 29 CFR 1910.178(g)(2). The source of this standard is National Fire Protection Association No. 505 - 1969: Powered Industrial Trucks, Section 700--Changing and Charging Storage Batteries.
"Adequate ventilation" as used in the indicated standard means providing natural, mechanical--general, or mechanical dilution ventilation sufficient to limit the accumulation of hydrogen gas in air at the charging site to levels below the lower explosive limit (4.1%).
A "typical exhaust fan" could meet this requirement if it were used in a manner such that the concentrations of the hydrogen gas in the fan's ambient air never exceeded the lower explosive limit.
Thank you for your interest in a safe workplace.
DAVID H. RHONE
|Standard Interpretations - Table of Contents|
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.