Standard Cited: 5A0001 OSH Act General Duty Paragraph
|Nr: 310988712||Citation: 02002||Issuance: 07/25/2008||ReportingID: 0418400|
|Viol Type:||Willful||NrInstances:||4||Contest Date:||07/25/2008|
|Abatement Date:||08/04/2008 X||Nr Exposed:||40||Final Order:||07/07/2010|
|Current Penalty:||$70,000.00||Gravity:||10||Haz Category:||DUST&FUMES|
|Penalty and Failure to Abate Event History|
|Penalty||F: Formal Settlement||07/07/2010||$70,000.00||08/04/2008||Willful|
Text For Citation: 02 Item/Group: 002 Hazard: DUST&FUMES
P.L. 91-596 Section 5(a)(1) of the Occupational Safety and Health Act of 1970: The employer does not furnish to each of his employees employment and a place of employment which are free from the recognized hazards of the propagation of a fire, deflagration, and/or explosion outside the area of the initial fire, deflagration, and/or explosion which are causing or likely to cause death or serious physical harm to employees: a.South Packing House & Bosch Packing House - On or about 02/07/2008, bucket elevator legs ("legs") or portions of legs that were located inside were not equipped with explosion relief venting to prevent secondary dust explosions and/or rupture of the elevator housing. b.South Packaging House; Bosch Packing House; Production Hummer Room (5th floor); 4th floor of Bulk Sugar Building; Powder Mill Room (4th floor South Packing House); and Top of Silos #1, #2, & #3 (9th Floor) - On or about 02/07/2008, rooms, buildings, or other enclosures were not provided with explosion relief venting distributed over the exterior walls and roof to prevent structural failures in the event of a dust explosion. c.Screw augers ("scrolls") transferring sugar from the 4th floor South Packing House to 4th floor Bulk Sugar Station and scrolls transporting sugar from 4th floor Bulk Station to "J-Bin" - On or about 02/07/2008, screw conveyors were not equipped with deflagration prevention devices such as, but not limited to deflagration/explosion relief venting, containment, isolation, or suppression to prevent the continued propagation of a flame front and overpressure into adjacent buildings/structures or areas and/or rupture of the equipment. d.South Packing House, 4th floor Powder Mill Room - On or about 02/07/2008, pulverizers and atomizers were not equipped with explosion prevention devices such as, but not limited to deflagration/explosion relief venting, containment, isolation, or suppression to prevent the continued propagation of a flame front and overpressure into adjacent buildings/structures/areas and/or rupture of the equipment. One feasible means of abatement would be to design and install appropriate deflagration/explosion protection systems for all sugar conveyance and processing equipment, as referenced in National Fire Protection Association (NFPA) 61, 2008 & 2002 edition, Chapter 4, Construction Requirements, paragraph 4.1.2; Chapter 6, Ventilation and Venting, paragraphs 6.2.1 and 6.3.1; and Chapter 7, Equipment, paragraph 188.8.131.52. Pursuant to 29 C.F.R. 1903.19, within ten (10) calendar days, the employer must submit an abatement plan describing the actions it is taking to ensure that appropriate explosion relief venting, deflagration devices and explosion prevention devices are installed.
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.