June 28, 1989
The Dallas Regional Office has brought to our attention possible ineffective Square D, two-pole QO-GFI circuit breakers due to a faulty electronic component.
The manufacturer, Square D Company, has discovered that an electronic component of the two-pole, QO-GFI circuit breakers, series 1 may fail prematurely. While the unit continues to function as a switch, the failure of the electronic component renders the ground fault interrupting feature inoperable. This condition gives the user of the two-pole QO-GFI circuit breaker false sense of protection and may expose workers to electrical shocks from faulty equipment.
Square D had issued a product recall notice to contractors. The notice identified the two-pole QO-GFI circuit breakers manufactured between March 1982 and December 1986 as the defective ones. Square D, in its recall notice, listed the following "Quick Open" and "Quick Open Bolted" circuit breakers with amperage from 215 to 230:
The two pole QO-GFI circuit breaker occupies two positions in the panel board. It is easily recognized by the yellow "Push to Test" button and a trip indicator. There is no Square D symbol next to the "Push to Test" button for the series 1 circuit breakers. Square D wants all two pole QO-GFI series 1 circuit breakers returned.
The recall was completed on June 30, 1988 and Square D has indicated that most faulty QO and QOB-GFI circuit breakers have been returned. However, some may still be in use. We recommend that compliance and consultation personnel be aware of the hazard addressed in this bulletin.
Please disseminate this information to Area Offices, State Plan States, and Consultation Project Offices.Back to Top
The Department of Labor does not endorse, takes no responsibility for, and exercises no control over the linked organization or its views, or contents, nor does it vouch for the accuracy or accessibility of the information contained on the destination server. The Department of Labor also cannot authorize the use of copyrighted materials contained in linked Web sites. Users must request such authorization from the sponsor of the linked Web site. Thank you for visiting our site. Please click the button below to continue.