When working on or with overhead lines the provisions of paragraphs (a) (2) through (8) of this
section shall be complied with in addition to other applicable provisions of this subpart.
Prior to climbing poles, ladders, scaffolds, or other elevated structures, an inspection shall be
made to determine that the structures are capable of sustaining the additional or unbalanced stresses to which they will be subjected.
Where poles or structures may be unsafe for climbing, they shall not be climbed until made safe by
guying, bracing, or other adequate means.
Before installing or removing wire or cable, strains to which poles and structures will be subjected
shall be considered and necessary action taken to prevent failure of supporting structures.
When setting, moving, or removing poles using cranes, derricks, gin poles, A-frames, or other
mechanized equipment near energized lines or equipment, precautions shall be taken to avoid contact with energized lines or equipment, except in
bare-hand live-line work, or where barriers or protective devices are used.
Equipment and machinery operating adjacent to energized lines or equipment shall comply with
Unless using suitable protective equipment for the voltage involved, employees standing on the
ground shall avoid contacting equipment or machinery working adjacent to energized lines or equipment.
Lifting equipment shall be bonded to an effective ground or it shall be considered energized and
barricaded when utilized near energized equipment or lines.
Pole holes shall not be left unattended or unguarded in areas where employees are currently
Tag lines shall be of a nonconductive type when used near energized lines.
Metal tower construction.
When working in unstable material the excavation for pad- or pile-type footings in excess of 5 feet
deep shall be either sloped to the angle of repose as required in 1926.652 or shored if entry is required. Ladders shall be provided for access to
pad- or pile-type footing excavations in excess of 4 feet.
When working in unstable material provision shall be made for cleaning out auger-type footings
without requiring an employee to enter the footing unless shoring is used to protect the employee.
A designated employee shall be used in directing mobile equipment adjacent to footing
No one shall be permitted to remain in the footing while equipment is being spotted for
Where necessary to assure the stability of mobile equipment the location of use for such
equipment shall be graded and leveled.
Tower assembly shall be carried out with a minimum exposure of employees to falling objects when
working at two or more levels on a tower.
Guy lines shall be used as necessary to maintain sections or parts of sections in position and
to reduce the possibility of tipping.
Members and sections being assembled shall be adequately supported.
When assembling and erecting towers the provisions of paragraphs (b)(5)(i), (ii) and (iii) of this
section shall be complied with:
The construction of transmission towers and the erecting of poles, hoisting machinery, site
preparation machinery, and other types of construction machinery shall conform to the applicable requirements of this part.
No one shall be permitted under a tower which is in the process of erection or assembly, except
as may be required to guide and secure the section being set.
When erecting towers using hoisting equipment adjacent to energized transmission lines, the
lines shall be deenergized when practical. If the lines are not deenergized, extraordinary caution shall be exercised to maintain the minimum
clearance distances required by 1926.950(c), including Table V-1.
Erection cranes shall be set on firm level foundations and when the cranes are so equipped
outriggers shall be used.
Tag lines shall be utilized to maintain control of tower sections being raised and positioned,
except where the use of such lines would create a greater hazard.
The loadline shall not be detached from a tower section until the section is adequately
Except during emergency restoration procedures erection shall be discontinued in the event of
high wind or other adverse weather conditions which would make the work hazardous.
Equipment and rigging shall be regularly inspected and maintained in safe operating
Adequate traffic control shall be maintained when crossing highways and railways with equipment as
required by the provisions of 1926.200(g)(1) and (2).
A designated employee shall be utilized to determine that required clearance is maintained in moving
equipment under or near energized lines.
Stringing or removing deenergized conductors.
When stringing or removing deenergized conductors, the provisions of paragraphs (c)(2) through (12)
of this section shall be complied with.
Prior to stringing operations a briefing shall be held setting forth the plan of operation and
specifying the type of equipment to be used, grounding devices and procedures to be followed, crossover methods to be employed, and the clearance
Where there is a possibility of the conductor accidentally contacting an energized circuit or
receiving a dangerous induced voltage buildup, to further protect the employee from the hazards of the conductor, the conductor being installed or
removed shall be grounded or provisions made to insulate or isolate the employee.
If the existing line is deenergized, proper clearance authorization shall be secured and the line
grounded on both sides of the crossover or, the line being strung or removed shall be considered and worked as energized.
When crossing over energized conductors in excess of 600 volts, rope nets or guard structures
shall be installed unless provision is made to isolate or insulate the workman or the energized conductor. Where practical the automatic reclosing
feature of the circuit interrupting device shall be made inoperative. In addition, the line being strung shall be grounded on either side of the
crossover or considered and worked as energized.
Conductors being strung in or removed shall be kept under positive control by the use of adequate
tension reels, guard structures, tielines, or other means to prevent accidental contact with energized circuits.
Guard structure members shall be sound and of adequate dimension and strength, and adequately
Catch-off anchors, rigging, and hoists shall be of ample capacity to prevent loss of the
The manufacturer's load rating shall not be exceeded for stringing lines, pulling lines, sock
connections, and all load-bearing hardware and accessories.
Pulling lines and accessories shall be inspected regularly and replaced or repaired when
damaged or when dependability is doubtful. The provisions of 1926.251(c)(4)(ii) (concerning splices) shall not apply.
Conductor grips shall not be used on wire rope unless designed for this application.
While the conductor or pulling line is being pulled (in motion) employees shall not be permitted
directly under overhead operations, nor shall any employee be permitted on the crossarm.
A transmission clipping crew shall have a minimum of two structures clipped in between the crew and
the conductor being sagged. When working on bare conductors, clipping and tying crews shall work between grounds at all times. The grounds shall
remain intact until the conductors are clipped in, except on dead end structures.
Except during emergency restoration procedures, work from structures shall be discontinued when
adverse weather (such as high wind or ice on structures) makes the work hazardous.
Stringing and clipping operations shall be discontinued during the progress of an electrical
storm in the immediate vicinity.
Reel handling equipment, including pulling and braking machines, shall have ample capacity,
operate smoothly, and be leveled and aligned in accordance with the manufacturer's operating instructions.
Reliable communications between the reel tender and pulling rig operator shall be
Each pull shall be snubbed or dead ended at both ends before subsequent pulls.
Stringing adjacent to energized lines.
Prior to stringing parallel to an existing energized transmission line a competent determination
shall be made to ascertain whether dangerous induced voltage buildups will occur, particularly during switching and ground fault conditions. When
there is a possibility that such dangerous induced voltage may exist the employer shall comply with the provisions of paragraphs (d) (2) through (9)
of this section in addition to the provisions of paragraph (c) of this 1926.955, unless the line is worked as energized.
When stringing adjacent to energized lines the tension stringing method or other methods which
preclude unintentional contact between the lines being pulled and any employee shall be used.
All pulling and tensioning equipment shall be isolated, insulated, or effectively grounded.
A ground shall be installed between the tensioning reel setup and the first structure in order to
ground each bare conductor, subconductor, and overhead ground conductor during stringing operations.
During stringing operations, each bare conductor, subconductor, and overhead ground conductor shall
be grounded at the first tower adjacent to both the tensioning and pulling setup and in increments so that no point is more than 2 miles from a
The grounds shall be left in place until conductor installation is completed.
Such grounds shall be removed as the last phase of aerial cleanup.
Except for moving type grounds, the grounds shall be placed and removed with a hot
Conductors, subconductors, and overhead ground conductors shall be grounded at all dead-end or
A ground shall be located at each side and within 10 feet of working areas where conductors,
subconductors, or overhead ground conductors are being spliced at ground level. The two ends to be spliced shall be bonded to each other. It is
recommended that splicing be carried out on either an insulated platform or on a conductive metallic grounding mat bonded to both grounds. When a
grounding mat is used, it is recommended that the grounding mat be roped off and an insulated walkway provided for access to the mat.
All conductors, subconductors, and overhead ground conductors shall be bonded to the tower at any
isolated tower where it may be necessary to complete work on the transmission line.
Work on dead-end towers shall require grounding on all deenergized lines.
Grounds may be removed as soon as the work is completed: Provided, That the line is not left
open circuited at the isolated tower at which work is being completed.
When performing work from the structures, clipping crews and all others working on conductors,
subconductors, or overhead ground conductors shall be protected by individual grounds installed at every work location.
Live-line bare-hand work. In addition to any other applicable standards contained elsewhere in this
subpart all live-line bare-hand work shall be performed in accordance with the following requirements:
Employees shall be instructed and trained in the live-line bare-hand technique and the safety
requirements pertinent thereto before being permitted to use the technique on energized circuits.
Before using the live-line bare-hand technique on energized high-voltage conductors or parts, a
check shall be made of:
The voltage rating of the circuit on which the work is to be performed;
The clearances to ground of lines and other energized parts on which work is to be performed;
The voltage limitations of the aerial-lift equipment intended to be used.
Only equipment designed, tested, and intended for live-line bare-hand work shall be used.
All work shall be personally supervised by a person trained and qualified to perform live-line
The automatic reclosing feature of circuit interrupting devices shall be made inoperative where
practical before working on any energized line or equipment.
Work shall not be performed during the progress of an electrical storm in the immediate
A conductive bucket liner or other suitable conductive device shall be provided for bonding the
insulated aerial device to the energized line or equipment.
The employee shall be connected to the bucket liner by use of conductive shoes, leg clips, or
other suitable means.
Where necessary, adequate electrostatic shielding for the voltage being worked or conductive
clothing shall be provided.
Only tools and equipment intended for live-line bare-hand work shall be used, and such tools and
equipment shall be kept clean and dry.
Before the boom is elevated, the outriggers on the aerial truck shall be extended and adjusted to
stabilize the truck and the body of the truck shall be bonded to an effective ground, or barricaded and considered as energized equipment.
Before moving the aerial lift into the work position, all controls (ground level and bucket) shall
be checked and tested to determine that they are in proper working condition.
Arm current tests shall be made before starting work each day, each time during the day when higher
voltage is going to be worked and when changed conditions indicate a need for additional tests. Aerial buckets used for bare-hand live-line work shall
be subjected to an arm current test. This test shall consist of placing the bucket in contact with an energized source equal to the voltage to be
worked upon for a minimum time of three (3) minutes. the leakage current shall not exceed 1 microampere per kilo-volt of nominal line-to-line voltage.
Work operations shall be suspended immediately upon any indication of a malfunction in the equipment.
All aerial lifts to be used for live-line bare-hand work shall have dual controls (lower and upper)
as required by paragraph (e)(12)(i) and (ii) of this section.
The upper controls shall be within easy reach of the employee in the basket. If a two basket
type lift is used access to the controls shall be within easy reach from either basket.
The lower set of controls shall be located near base of the boom that will permit over-ride
operation of equipment at any time.
Ground level lift control shall not be operated unless permission has been obtained from the
employee in lift, except in case of emergency.
Before the employee contacts the energized part to be worked on, the conductive bucket liner shall
be bonded to the energized conductor by means of a positive connection which shall remain attached to the energized conductor until the work on the
energized circuit is completed.
The minimum clearance distances for live-line bare-hand work shall be as specified in Table V-2.
These minimum clearance distances shall be maintained from all grounded objects and from lines and equipment at a different potential than that to
which the insulated aerial device is bonded unless such grounded objects or other lines and equipment are covered by insulated guards. These distances
shall be maintained when approaching, leaving, and when bonded to the energized circuit.
TABLE V-2 - MINIMUM CLEARANCE DISTANCES FOR LIVE-LINE
BARE-HAND WORK (ALTERNATING CURRENT)
| Distance in feet and inches
Voltage range (phase to | for maximum voltage
phase) kilovolts |__________________________________
| Phase to ground | Phase to phase
2.1 to 15 ..................| 2'0" | 2'0"
15.1 to 35 .................| 2'4" | 2'4"
35.1 to 46 .................| 2'6" | 2'6"
46.1 to 72.5 ...............| 3'0" | 3'0"
72.6 to 121 ................| 3'4" | 4'6"
138 to 145 .................| 3'6" | 5'0"
161 to 169 .................| 3'8" | 5'6"
230 to 242 .................| 5'0" | 8'4"
345 to 362 .................| (1)7'0" | (1)13'4"
500 to 552 .................| (1)11'0" | (1)20'0"
700 to 765 .................| (1)15'0" | (1)31'0"
Footnote(1) For 345-362kv., 500-552kv., and 700-765kv., the minimum
clearance distance may be reduced provided the distances are not made
less than the shortest distance between the energized part and the
When approaching, leaving, or bonding to an energized circuit the minimum distances in Table V-2
shall be maintained between all parts of the insulated boom assembly and any grounded parts (including the lower arm or portions of the
When positioning the bucket alongside an energized bushing or insulator string, the minimum
line-to-ground clearances of Table V-2 must be maintained between all parts of the bucket and the grounded end of the bushing or insulator
The use of handlines between buckets, booms, and the ground is prohibited.
No conductive materials over 36 inches long shall be placed in the bucket, except for
appropriate length jumpers, armor rods, and tools.
Nonconductive-type handlines may be used from line to ground when not supported from the
The bucket and upper insulated boom shall not be overstressed by attempting to lift or support
weights in excess of the manufacturer's rating.
A minimum clearance table (as shown in table V-2) shall be printed on a plate of durable
nonconductive material, and mounted in the buckets or its vicinity so as to be visible to the operator of the boom.
It is recommended that insulated measuring sticks be used to verify clearance