Rubber protective equipment shall be in accordance with the provisions of the American National
Standards Institute (ANSI), ANSI J6 series, as follows:
Item | Standard
Rubber insulating gloves .......................| J6.6-1971.
Rubber matting for use around electric |
apparatus ....................................| J6.7-1935 (R1971).
Rubber insulating blankets .....................| J6.4-1971.
Rubber insulating hoods ........................| J6.2-1950 (R1971).
Rubber insulating line hose ....................| J6.1-1950 (R1971).
Rubber insulating sleeves ......................| J6.5-1971.
Rubber protective equipment shall be visually inspected prior to use.
In addition, an "air" test shall be performed for rubber gloves prior to use.
Protective equipment of material other than rubber shall provide equal or better electrical and
Protective hats shall be in accordance with the provisions of ANSI Z89.2-1971 Industrial Protective
Helmets for Electrical Workers, Class B, and shall be worn at the jobsite by employees who are exposed to the hazards of falling objects, electric
shock, or burns.
Personal climbing equipment.
Body belts with straps or lanyards shall be worn to protect employees working at elevated locations
on poles, towers, or other structures except where such use creates a greater hazard to the safety of the employees, in which case other safeguards
shall be employed.
Body belts and safety straps shall meet the requirements of 1926.959. In addition to being used as
an employee safeguarding item, body belts with approved tool loops may be used for the purpose of holding tools. Body belts shall be free from
additional metal hooks and tool loops other than those permitted in 1926.959.
Body belts and straps shall be inspected before use each day to determine that they are in safe
Lifelines and lanyards shall comply with the provisions of 1926.502.
Safety lines are not intended to be subjected to shock loading and are used for emergency rescue
such as lowering a man to the ground. Such safety lines shall be a minimum of one-half-inch diameter and three or four strand first-grade manila or
its equivalent in strength (2,650 lb.) and durability.
Defective ropes shall be replaced.
Portable metal or conductive ladders shall not be used near energized lines or equipment except as
may be necessary in specialized work such as in high voltage substations where nonconductive ladders might present a greater hazard than conductive
ladders. Conductive or metal ladders shall be prominently marked as conductive and all necessary precautions shall be taken when used in specialized
Hook or other type ladders used in structures shall be positively secured to prevent the ladder from
being accidentally displaced.
Only live-line tool poles having a manufacturer's certification to withstand the following minimum
tests shall be used:
100,000 volts per foot of length for 5 minutes when the tool is made of fiberglass; or
75,000 volts per foot of length for 3 minutes when the tool is made of wood; or
Other tests equivalent to paragraph (d) (i) or (ii) of this section as appropriate.
All live-line tools shall be visually inspected before use each day. Tools to be used shall be wiped
clean and if any hazardous defects are indicated such tools shall be removed from service.
Measuring tapes or measuring ropes. Measuring tapes or measuring ropes which are metal or contain
conductive strands shall not be used when working on or near energized parts.
Switches for all powered hand tools shall comply with 1926.300(d).
All portable electric handtools shall:
Be equipped with three-wire cord having the ground wire permanently connected to the tool frame
and means for grounding the other end; or
Be of the double insulated type and permanently labeled as "Double Insulated"; or
Be connected to the power supply by means of an isolating transformer, or other isolated power
All hydraulic tools which are used on or around energized lines or equipment shall use nonconducting
hoses having adequate strength for the normal operating pressures. It should be noted that the provisions of 1926.302(d)(2) shall also
All pneumatic tools which are used on or around energized lines or equipment shall:
Have nonconducting hoses having adequate strength for the normal operating pressures,
Have an accumulator on the compressor to collect moisture.
[59 FR 40730, Aug. 9, 1994]